Distribution elements are used as terminal components of ventilation ducts and for airflow directing or regulation. The most used in bathrooms and toilet rooms are dish valves that we offer several types (plastic, metal, supply, exhaust, universal...). Other elements that are frequently used are nozzles, anemostats and diffusers for both circular and rectangular ducts.
Dish valves are the most frequently used for air exhaustion from sanitary facilities. However, they can be also used for air supply. There are also available universal dish valves determined both for supply and exhaust air in our assortment. The valve is composed of an inlet cone and of an adjustable central disc enabling the air flow regulation. Dish valves work with relatively low air flows from 30 to 200 m3/h. They are manufactured in diameters from 80 to 200 mm and are made of plastic or of standardly varnished sheet steel.
Anemostats are ventilation terminal components determined for the air distribution in commercial and residential premises. Their outflow surface is composed of fixed profiled blades (the circular construction ensures an even airflow into all directions) or of adjustable profiled blades (by changing the outflow angle is provided an intensive mixing of the supply air).
Diffusers are ventilation terminal distribution components used to supply and exhaust the air in offices, hotels, family houses and the like. Diffusers are characterised by a simple airflow regulation and by a modern design. Diffusers are primarily manufactured from galvanized metal sheet and are standardly varnished in the white tone RAL.
Long-reach nozzles are the most suitable distribution components for air distribution over long distances intended for premises such as sports and industrial halls, commercial centres, airports and other public premises. Nozzles are intended for placement into ceiling or wall for the air supply. There are fixed, adjustable, jet and multi-nozzles in our assortment.
Grilles / Vents
Vents are the most employed distribution components in the industrial ventilation and are installed directly on the duct - circular or four-sided. Ducts are available in a single-row or double-row variant depending on the number of rows of the adjustable blades. The single-row vents are intended to be installed for the exhaust air and the double-row for its supply. The vents can be equipped by various types of regulation depending on an individual request.